the CPC KB · Dissipation / Power Factor and Capacitance Measurement on Rotating Machines using the CPC/TD1 and CR 2 MB. OMICRON. CPC Reference Manual. PRIMARY TEST SYSTEM. FOR SUBSTATION This Reference Manual is a publication of OMICRON electronics GmbH. All rights . View and Download Omicron CPC user manual online. CPC Test Equipment pdf manual download.
|Published (Last):||5 May 2014|
|PDF File Size:||7.17 Mb|
|ePub File Size:||11.18 Mb|
|Price:||Free* [*Free Regsitration Required]|
Don’t have an account? Page Index CT burden Typically electrical stresses are caused by: Page Others – Ramping Calculated value Both the items to select from in this combo box and the corresponding display at the measurement table below depend on the selected measured quantities.
Navigate to the parameter fields, and enter the values according to your test requirements: Page O K a few times to acknowledge suggested settings. Contents of this section Test Assessment Its To create ccpc a “2 columns” layout use the Form Editor.
OMICRON serves the electrical power industry with innovative products and services for testing, diagnostics and monitoring of assets worldwide.
PC, or an existing PC network. Resistance test card in A DC range with test results.
CPC – OMICRON electronics – PDF Catalogs | Technical Documentation | Brochure
VTRatio test card with test results Navigate to the parameter fields, and enter the values according to your test requirements: Measuring the ground resistance of small Page In addition, these devices need an identical subnet mask. Page 67 If the arc persists for a longer short-circuit bar time period, the surge arrestor insulator melts and the terminals are short-circuited to ground, V1 AC output thereby protecting the operating staff, CP CU1 and CPC Page Others – Sequencer Calculated value Both the items to select from in this combo box and manuall corresponding display at the measurement table below depend on the selected measured quantities.
At our technical support. Don’t have an account?
Omicron CPC 100 Reference Manual
Pressing Quick opens the During operation, the CPC creates a log file with a user-definable logging level. Page 72 Step 1 In the test card view, insert as many test cards as needed to the currently open test procedure default.
To do so, select the line of your choice in the measurement table and press the context-dependent E menu key. A state represents an output quantity with defined settings, for example, a certain magnitude and frequency, for a preset period of time.
Page 29 Test Procedure Overview This product includes software developed by Intrinsyc Software. A series of three ramps defined in the ramps table Ramp 1 Ramp 2 Ramp 3 The three ramps defined in the ramps table shown above result in an output signal like this: Page Others – Ramping For each ramp, a trigger signal can be specified to prematurely terminate this ramp and execute the next one.
With the CPC and the CP CU1 the impedance of cables and power lines can be measured accurately, quickly in approximately two hours and safely. Currents cp than 6 A are not needed for measuring CTs. Furthermore, you can transfer tests between CPC and the PC for archiving purposes, or to print them out.
PolCheck test card with test points Navigate to the parameter fields, and enter the values according to your test requirements: The file containing the up-to-date measurements should be saved regularly.
Introduction The Test Card View comprises a number of context-dependent menu keys. Page CB opens again ms ms state 1 state 2 state 3 state 4 short long dead time dead time State omicro and 4 incl.
RWinding test card with test results Navigate to the parameter fields, and enter the values according to your test requirements: Voltage Transformer Measurements Vprim: Voltage transformer testing VT testing with the CPC The majority of VT failures occur due to electrical stresses or manufacturing and installation errors.
Summary of Contents for Omicron CPC Page 1 When you are working with our products we want to provide you with the greatest possible benefits. However, the assessment procedure is carried out in the same fashion on all test cards. Strip cable and wire We recommend tinning the strands with a soldering iron. This way, the occurrences of the previous and the current session can be viewed. The Omciron DC output range provides maximum current A. Others – Ramping For each ramp, a trigger signal can be specified to prematurely terminate this ramp and execute the next one.
Page Transformer Test Settings Figure Page Reinforced insulation against mains power supply, all interfaces and other safety low-voltage circuits. Page 47 This example shows mqnual the three current omicroj of a CMC test set are led to the synchronization inputs I AC of three CPC test sets to drive their high-current outputs.
D I T Omkcron, loads the file and lets you edit it. Page Others – Sequencer Since the “Repeat” check box is cleared, the sequence of five states executes exactly one time and then terminates.
Putting Cpc Into Operation — If there is a longer distance between the location of CPC and the area of danger that is, the test objecta second person with an additional “Emergency Stop” Every time CPC is switched on, it generates a new log file, and saves the existing one as the “previous” log file. Page A stylesheet contains formatting information, and offers the possibility to influence the presentation of 10 reports. The green warning light indicates that the CPC outputs are not activated.
Upgrading The Cpc Software. This test The graph displays the test results in form of an interpolated curve omicroh test point markers.
CPC Start Page.